Call (214) 351-7030 for AC Repair, Installation & More
Is your Dallas air conditioning system prepared for 100-degree weather? You need your system installed with precision, maintained with professional-level skill, and repaired swiftly and accurately when needed. If you’re looking for air conditioner services in Dallas, you’ve come to the right service team.
Barbosa Plumbing & Air Conditioning is a full-service air conditioning company serving Dallas and the surrounding areas. For 40 years we’ve been offering top-quality services, dependable results, and customized cooling services that strive to suit the unique needs of each client.
Our air conditioning services include:
Looking for AC services in Dallas? Contact us online, or call (214) 351-7030 to schedule service with our team now!
AC Installation & Replacement in Dallas
Our technicians are certified, licensed, and local. We know precisely how to ensure you get a quality install, and how to make certain that your Dallas home gets the optimized cooling system that will suit your needs best. When you call on Barbosa Plumbing & Air Conditioning for air conditioner replacement and installation you can expect:
- Experienced and skilled AC contractors
- A top-quality air conditioner install that ensures optimal performance
- Maximized AC efficiency to help keep utility costs to a minimum
- A 100% satisfaction guarantee on our AC installation service
AC Repair in Dallas, TX
Struggling without a properly functioning cooling system for any amount of time is just not an option in our area. Our technicians use top-class diagnostic tools and honed skills in order to provide effective repairs that get you back to normalcy as soon as possible.
Call on our AC repair company when you’re experiencing:
- Drops in cooling performance
- Warm air coming from your vents
- Leaking around or on the indoor or outdoor AC unit
- Strange or loud, repetitive noises
- Increases in your monthly cooling costs
Need emergency air conditioner repair or a trained professional for AC troubleshooting? Call (214) 351-7030 or schedule AC repair online!
Complete Air Conditioner Maintenance in Dallas
It’s always best to avoid trouble and costly repairs, rather than deal with them as they come. Our air conditioning system technicians provide a streamlined and comprehensive tune-up and maintenance service to help keep your system performing on the level it was when you first had it installed. Our AC maintenance services will ensure that you:
- Pay less on your monthly cooling costs
- Avoid costly repairs and inconvenient breakdowns
- Enjoy a cooler, more comfortable home
- Are more likely to get the full life span from your AC system
Schedule Air Conditioning Services in Dallas!
As a quality HVAC company serving Dallas, we pride ourselves on our commitment to superior service, complete customer satisfaction, and helping our clients get the options that fit their needs best. When you want honest, dependable AC services in Dallas, Barbosa Plumbing & Air Conditioning is the team you can always count on!
Call (214) 351-7030 or schedule AC services in Dallas online any time!
for Dallas, TX
Our Reviews by City
Laura - Dallas, TX
Jonathan and Anthony were great. Very thorough and knowledgeable. Will definitely use them again. Did not overcharge.
Dom - Dallas, TX
Lucca was awesome, he was extremely professional, clean and polite. Fast at doing the job and explained everything really well. I would recommend him to anyone.
Prompt, efficient and effective
Wales - Dallas, TX
Jasmin - Dallas, TX
Lucys is always friendly and professional!
Always Great service!
Pat - Dallas, TX
Barbosa never fails for service! Jackie is very efficient and always friendly. I highly recommend Barbosa.
A bit pricey for not much work
Barbero - Dallas, TX
Scheduling was quick and easy, and everyone was very professional and polite. That's all I can say positive. I have used Barbosa before for an A/C not working, and they did a great job at a competitive price. I called them out this time for two problems - condensate water leak due to a broken PVC pipe and a bad thermostat. To replace the bad thermostat (with a new one that I provided) and to tell me they couldn't fix the PVC pipe without risking more damage to the unit, they charged me $280. That seems rather steep. They also looked at the system and told me many other potential problems, which I didn't ask them to do as I suspect being a pretty old system it is not perfect. It just seemed like the technician wanted me to replace the system when, apart from the two problems I mentioned, is working fine. As of now, Barbosa is batting .500, so I don't know if I would call them again if I need an A/C repair.
Terry does a neat job and gives good service
Killen - Dallas, TX
Responsive and efficient!
Louise - Dallas, TX
Shelby - Dallas, TX
They were very good and very professional
Waterman - Dallas, TX
For several years we have been greatly please with Barbosa service. Keep up the great work.
Great Customer Service!
George - Dallas, TX
fixed 2 problems
BobMounger - Dallas, TX
Terry did a great job, both problems were corrected rapidly & cost was within epxectations
James - Dallas, TX
on time, knowledgeable and pleasant service by Terry
Hainsfurther - Dallas, TX
Jen also did a good scheduling the service
Crawley - Dallas, TX
No matter what the problem, Terry has the answer and when he done I am sure the job is correct
No heat upstairs, system has various airflow issues
No Heat call for commercial build, arrived on site, investigated problem, found recently installed thermostat had failed, removed and replaced thermostat, tested system, left operational
NORITZ coding out on fault code 29 Removed water from neutralizer located inside tankless, removed neutralizer from tankless cabinet inspected, tested for proper drainage. Found condensation line backed up, condensation line of tankless connects to the condensation line of the upstairs and downstairs air conditioners. Cut the condensation line between the tankless water heater and the furthest A/C evaporator coil, water poured into plastic Bin that had been placed underneath the condensate line. Condensate line was blocked by debris from the air conditioners, materials such as rusty, dust and etc. Recommend separating the condensate line of the tankless from the air conditioners
New Gas Yard Service - pulled permit from City of Dallas
Fall Maintenance Inspection Performed - Check for Proper Operation Check Pilot Ignition sequence - Adjust pilot if necessary Observe Main Burner Operation Check the flue draft on natural draft furnaces Test fan switch / heating fan relay operation Check primary limit operation Cycle furnace off and record "fan off" temperature Visually Inspect heat excanger Check blower wheel for cleanliness Check blower motor , if applicable oil bearings, check belt bearings and pulley Check air filter and air cleaner and or replace filter if agreement requires Check furnace temperature rise Operate furnace and leak-check gas line from manual safety shut off valve to main burners Test Flue spill switch operation Check auxiliary limit switch operation Test Draft safeguard switch operation Perform combustion air test to ensure that there is enough ventilation to replace air for combustion Check humidifier operation Operate the furnace through one complete cycle
Gas pressure test performed - Does not include any repairs Repaired Bell Reducer, pulled permit with City of Dallas
Perform drain cleaning on master vanity and hall guest vanity. Master bathroom is now flowing fully but hall vanity is still flowing kind of slow. I Misc leak search on dish washer. Found leaking from part under dishwasher. Marked part with sharpie. Performed minor leak search for methane smell in master bathroom. Found nothing in visual inspection. Recommend preforming a hydrostatic test
Homeowner had concerns of furnace being too loud that we at Barbosa Plumbing recently installed, found supply vent located near the kitchen closed, opened vent and noise level reduced, investigated further found air filter completely blocked with paint, homeowner recently had kitchen cabinets painted, replaced air filter, left system operational
Performed heat inspection
Gas pressure test
Gas leak test.